The best way to Alter the MPI Node Deal with For any Siemens S7300 PLC

I've seven Siemens S7-300 PLCs related [http://hemoroiziforum.ro/discussion/226380/plc-movementplc-movement ? pac rx3i ]  collectively utilizing the MPI (Multi Position Interface) interface. The Siemens MPI protocol is used by Siemens PLCs to speak with exterior products. I would like to rename every single in the 7 PLCs. Listed below are the actions to accomplish that endeavor.

To start with, hook up your MPI cable on the 1st PLC. I'll be connecting my notebook to every PLC independently. Electricity up the PLC and open Simatic Supervisor. The "New Project" Wizard window will open. Just simply click Cancel to shut the window. Now click the Accessible Nodes icon about the toolbar. A window will open up displaying the identification of the PLC you will be connected to. My window is demonstrating MPI = two(instantly). Come up with a take note of the handle and shut the window.

Next we need to download a hardware configuration into the PLC. This is where we will rename the PLC node handle. You'll find probably a few of different solutions to do this - following is how I accomplish this. All seven of my PLCs tend to be the identical product; thus, I am applying the exact same hardware configuration. To the evident reasons, I would like to present just about every another MPI node tackle. I've a task file that contains all 7 of my PLC systems and a person components configuration file. I open up the a person components configuration file, and after that double click on Components within the suitable hand window. This will likely open up the HW Configuration window. During this window you should see your PLC with its MPI deal with offered.

Recall after we clicked the Available Nodes icon and saw MPI = 2(immediately)? My Components Configuration Window is showing a MPI address of seven. Spot your mouse cursor about the 7 and double simply click. Your CPU Houses window will open up. It ought to open into the Normal tab. Glimpse down and you may see Interface Form MPI by having an address of 7. Click Attributes as well as the MPI interface Houses window will open up. Employing the pull down menu, opt for your MPI node deal with and make sure the MPI (one) 187.5kbps is highlighted and click on Okay. You happen to be now back again to the CPU Houses window in which you will see your handle has improved. Simply click Ok and you'll go back to the Really hard Ware window in which you can validate your MPI node address has modified.

You are going to now simply click the Help you save and Compile icon and afterwards click the down load icon. The Select Concentrate on Module window will open up. Click on Okay plus the Find Node Address window will open up. In this article you will note the MPI node handle you assigned before. You will have to click the See button correct down below this. You will note the current node deal with surface, this could be the exact same as what you saw previously whenever you clicked the Obtainable Nodes icon. Just simply click on this number and you will see it show up inside the MPI handle slot underneath the Enter connection to target station. Click Ok and the Down load to Module window will open. Simply click Okay and the Prevent Goal Modules window will open. Click on Ok and the "Do you wish to start out the module?" window will open. Click Certainly.